Case History: Power Plant Balance of Plant, BOP #1
Last Updated: 05/10/2017
A Mid-Western Power Company had a requirement to permanently monitor four (4) FD (Forced Draft), five (5) ID (Induced Draft) and six (6) PA (Primary Air) Fans. The fifteen (15) Fans were spread across two (2) generating units located next to each other. The customer wanted to make use of their existing DCS and Plant Historian System for each unit. Two (2) existing Fiber Cables from the DCS to the general area of the machines were not being currently used. The customer required that the 2 Units be entirely separate systems.
As the Fans are of heavy rotor, light case design equipped with Journal Bearings the customer determined that they would use 239 bearing mounted 100 mv/g Accelerometers and wanted displayed values and trends to be in terms of Velocity (in/sec) in the plants DCS and Historian. The 5 VFD (Variable Frequency Drive) ID Fans had an additional requirement for Speed Sensor and Transmitter as the existing speed systems were not functioning dependably.
An additional requirement was that the proposed system must be able to withstand an outdoor environment with winter temperatures down to a worst case of -27 degrees F (32.78 degrees C).
A distributed system using 15 painted steel insulated enclosures was engineered to minimize sensor cabling and reduce installation costs. A thermal load calculation was completed for each enclosure and it was determined that insulated heated enclosures would be required. A thermostat was used to only turn on heaters when or if needed. It was determined that three (3) standard size enclosures would be used, 2 each 9 channel, 8 each 12 channel and 5 each 25 channel. Each enclosure included CMCP530 Velocity Transmitters, CMCP515 Power Supply, Field IO, Industrial Ethernet Switches, Heater, Thermostat and additionally for the 5 ID Fans, CMCP240 Speed Sensor and CMCP575 Speed Transmitter.
The CMCP530 Velocity Transmitters powers and accepts the 100 mv/g Accelerometer input and integrates the signal to a 4-20 mA Velocity signal. Each transmitters internal OK (Green LED) circuitry monitors the sensor bias voltages and drives the 4-20 mA signal to 0.00 mA on loss of OK.
Modbus TCP/IP was selected as the desired protocol for both Units. Enclosures were digitally linked using Cat5e cabling with a maximum allowed cable length of 100 meters between enclosures. Industrial Ethernet Cat5e to Fiber Converters were used to convert to the Fiber runs where required by length and back to the plant computers.
STI Vibration Monitoring Inc. completely assembled, integrated and tested each enclosure prior to shipment at its League City, Texas facility. IP addresses and Modbus buffer numbers were pre-assigned working with the customer.
9 Channel Enclosures: